Your shopping cart is empty!
MEDICAL GAS ALARM PANEL TECHNICAL SPECIFICATIONS
The pressure in the Hospital Central Gas System will be monitored 24 hours electronically by Pressure sensors (transducers).
The pressure status on the alarm panels shall be indicated by illuminated LEDs in the form of normal - high pressure and low pressure alarm conditions.
When the alarm panels rise or fall below 20% above the normal working pressure or vacuum level in the installation, they will give light and audible warning signals with LEDs.
Alarm panels are fully electronically controlled and must be designed as a separate electronic card for each gas. The power supply must be provided from the separate card.
There should be test and cancel buttons on the alarm panels. Cancel button should be set to temporarily stop the alarm panel sound.
The sensors must be connected to the installation directly or through capillary tubes. The alarm signal must be processed through the Sensors on the Electronic Cards and delivered to the Display Electronic Board. Mechanical Pressure switches will not be accepted due to difficulty in setting.
Supply voltage 220 V, 50 Hz. should be.
The alarm panels are designed for two or more gas services depending on the installation situation.
Alarm Panels must be CE Certified. Alarm Panels should be written in the scope of the document.
10. Manufacturer and producer companies should have ISO 9001: 2000 quality certificate.